The current would be 1000*602/(3*130) = 1543 A. This assumes the loads are equally balanced across the three phases.
I think you should also be considering some diversity as all your loads will not be operating at the same time.
You have already flagged this post. Clicking "Remove Flag" below will remove your flag, thus reducing the count by one as well.
Cable Sizing Software
Select, size and manage your power cables using myCableEngineering.
All your cables, all your projects.