# Power that can be used on copper wire

 Could you help me on the equivalent current of three phase alternating current having 400V , 530kW and the available cross-sectional area of a copper wire. Its length 350m for carrying this current. asked 7/2/2012 0

 To work out the current, you need the power factor (and efficiency if it is a motors, as your kW is the output power):  Current = 530,000/(3x230xpower factor), at a power factor of 0.95 = 808 A To understand the calculation, you can read the post: Three Phase Current - Simple Calculation  The cable size depends on the installation method and what voltage drop you will accept. You can use the sites cable sizing tool to work this out. answered 7/4/2012 Steven McFadyen 246

In order to provide an answer to this question, you must Login

## I am flagging this question because...

10 inform moderator flags remaining

## I am flagging this answer because...

10 inform moderator flags remaining

## Flagging a Post

You have already flagged this post. Clicking "Remove Flag" below will remove your flag, thus reducing the count by one as well.

## I am deleting this answer because...

Low Voltage Fault Tables

The following tables provide quick order of magnitude fault levels for a a range of typical low voltage situations.

Low Voltage Switchroom Design Guide

Low voltage (LV) switchrooms are common across all industries and one of the more common spatial requirements which need to be designed into a project...

IEC 61439 - The Switchgear Standard

The new standard IEC 61439 replaces the old 60439. Compared to the old standard, the new 61439 is a more clearly defined and takes into account the assembly...

Closed Doors

"I can live with doubt and uncertainty and not knowing. I think it is much more interesting to live not knowing than to have answers that might be wrong...

Batteries

A battery consists of one or more cells, each of which use stored chemical energy to produce electrical energy, There are many types of cells and these...

Introduction to Cathodic Protection

If two dissimilar metals are touching and an external conducting path exists, corrosion of one the metals can take place.  Moisture or other materials...

Understanding Circuit Breaker Markings

IEC 60947 is the circuit breaker standard and covers the marking of breakers in detail. Any manufacturer following this standard should comply with the...

Cable Sheath and Armour Loss

When sizing cables, the heat generated  by losses within any sheath or armour need to be evaluated. When significant, it becomes a factor to be considered...

Dielectric loss in cables

Dielectrics (insulating materials for example) when subjected to a varying electric field, will have some energy loss.   The varying electric field causes...