I wanted to verify my understanding was correct, that owing to the delta/star winding of most LV transformers, the fault level seen by the HV protection is 2/3 the fault level(converted to current at the primary voltage) as the fault experienced at LV for both 2phase and 3phase faults. I came across this info in a power system commissioning book published by theIEE; however am confused that this does not appear to be taken into consideration by software packages. If correct, then it would suggest the HV time current curve should be moved tothe right of the LV curves when they are displayed together and you are assessing discrimination across a transformer  with the fault immediately downstream on the main LV protective device... asked 9/26/2012 Rhys Jones2

 You are a wee-bit incorrect, I am afraid. In a delta connected primary of a delta/star trafo., only the phase current (i.e.) the current thro the windings would be about 56% of the line current. But, the protection system, even on the HV side, would only see the line current, which would be reduced at the HV side, by the turns ratio of the trafo. Why then, there should be a problem in co-ordination? answered 4/10/2013 EE65 19 Not sure where 2/3 comes from; it doesn't sound right to me. I think the primary fault level would be related to turns (voltage) ratio of the transformer. If you have for example a 240 MVA fault on the secondary, it will still be seen as a 240 MVA on the primary. The difference will be in the level of current (the secondary current being much bigger and the actual value being dependent on the voltages). If you can post an extract from the book, I can try to work out where to 2/3 came from. On protection curves, you are right - you do need to make sure all the curves are related to the same voltage (which would mean shifting any HV curves to the right on an LV plot). answered 9/30/2012 Steven McFadyen 246

In order to provide an answer to this question, you must Login

## I am flagging this question because...

10 inform moderator flags remaining

## I am flagging this answer because...

10 inform moderator flags remaining

## Flagging a Post

You have already flagged this post. Clicking "Remove Flag" below will remove your flag, thus reducing the count by one as well.

## I am deleting this answer because...

Welcome back Bottle

‘Kept looking at a card, y’see? Kept looking at it. Welcome back Bottle. Gods below welcome home. The Crippled God A Tale of the Malazan Book of the...

Post Authorship

In 2011, with the introduction of it’s Panda search ranking algorithms, Google introduced tools for determining the original author of posts.  The intention...

IEC 60287 Current Capacity of Cables - An Introduction

IEC 60287 "Calculation of the continuous current rating of cables (100% load factor)" is the International Standard which defines the procedures and equations...

Useful Motor Technical Information

Sometimes it’s useful to be able to quickly lookup a piece of technical information.  This note is a collection of information related to motors, and in...

What is LED?

Light Emitting Diodes (LED ) are increasing gaining favour in both the domestic and commercial sectors; due to their efficiency, sustainability and durability...

Three Phase Power Simplified

A single phase system is perhaps the most common type of system most people are familiar with. This is what people have in their homes and what appliances...

IEC 61439 Verification Methods

The (relatively new) switchgear and control gear standard, IEC 61439 'Low-voltage switchgear and controlgear assemblies' has three methods which can be...

Capacitor Theory

Capacitors are widely used in electrical engineering for functions such as energy storage, power factor correction, voltage compensation and many others...

Why use catalogues

I'm a fan of using manufacturers catalogues. There are two main reasons for this. Firstly, if your involved in the purchase of equipment, you will likely...

Laplace Transform

Laplace transforms and their inverse are a mathematical technique which allows us to solve differential equations, by primarily using algebraic methods...

Our website uses cookies so that we can provide a better experience.