Armour for Electrical Cables

 On what basis the type of armour(tape/ wire/steel/aluminium/cu etc) is selected for a given cable?. For example does it depend on frequency,volts,insulation,type of conductor,grounding facility,bending etc asked 10/19/2011 naban6

 The main purpose of armour is to provide mechanical protection, although it can also provide part of the earth fault path. For multi-core cables steel wire armour is most often used. Single core cables produce a magnetic field which induce current and losses in steel; aluminium being non-magnetic is used with these cables. It doesn’t really depend on voltage or frequency. At higher voltages you have higher magnetic fields which would give bigger problems if you used steel wire on a single core cable instead of aluminium. Earthing does not affect it; however you should always ensure the armour is earthed at a supply end, to prevent it becoming live in the event of a fault. answered 10/19/2011 Steven McFadyen 246

In order to provide an answer to this question, you must Login

I am flagging this question because...

10 inform moderator flags remaining

I am flagging this answer because...

10 inform moderator flags remaining

Flagging a Post

You have already flagged this post. Clicking "Remove Flag" below will remove your flag, thus reducing the count by one as well.

I am deleting this answer because...

Tips for a better Low Voltage Protection Discrimination Study

Carrying out a protection system discrimination study is critical to ensure the correct functioning of  the electrical system in the event of faults. ...

Restricted Earth Fault Protection

The windings of many medium and small sized transformers are protected by restricted earth fault (REF) systems. The illustration shows the principal of...

Laplace Transform

Laplace transforms and their inverse are a mathematical technique which allows us to solve differential equations, by primarily using algebraic methods...

IEEE Winds of Change

IEEE TV has a part series of videos on wind power and it's implication. For a really good overview to the technologies and issues around wind power, these...

Power Factor

Power factor is the ratio between the real power (P in kW) and apparent power (S in kVA) drawn by an electrical load. The reactive power (Q in kVAr)...

How D.C. to A.C. Inverters Work

Traditionally generation of electricity has involved rotating machines to produce alternating sinusoidal voltage and current (a.c. systems). With the development...

Wiki Depreciation

We have had the Wiki with us for a long time now, but at last I have decided to say bye bye – more details on why below.

Electromechanical Relays

Electromechanical relays have been the traditional backbone of electrical protection systems.  While over recent years these have been replaced by microprocessor...

UPS Sizing - Rules of Thumb

It wasn't so long ago I was telling someone that I don't use rules of thumb as most things are easily calculated anyhow.   As it turns out I last week...

International System of Units (SI System)

The International System of Units (abbreviated SI) is the world's most widely used system of units.  The system consists of a set of units and prefixes...

Our website uses cookies so that we can provide a better experience.