# Short Circuit Fault Current (comprehensive)

 Dear Sir, I have attached a snapshot of small sld in which the equivalent parameters shown. If we calculate the equivalent impedance of cable-0022 manually and add that value with thevEq value of 11kv bus-1 that does not match with the shown value of 11kv bus-3. Kindly help and thanks in advance. Yash Arora asked 8/1/2015 yash4

 Arora, It does look like something needs clarifying.  I get: > c22=sqrt(0.0431^2+0.0270^2) = 0.0509 > c22+1.3037 =  1.3546 1.3546 and not the 1.3335pu as expected. Are you sure there are not some missing parallel impedance not shown on the diagram?  It may also be that we are adding the impedances arithmetically and not vectorially - do you have R and X for the 11 kV busbars so that we can check this.  Other than the above, in this instance I would contact the software manufacturer and ask him why the results are not the same.  If you do this, please post his reply here for future reference.  Steven answered 8/2/2015 Steven McFadyen 246 Dear Mr. Steven, Thanks for spending your precious time to reply. Actually, there is no parallel impedance which can impact on the calculated values in the SLD. And I don't have R & X values of 11kV busbar. - yash 8/2/2015

In order to provide an answer to this question, you must Login

## I am flagging this question because...

10 inform moderator flags remaining

## I am flagging this answer because...

10 inform moderator flags remaining

## Flagging a Post

You have already flagged this post. Clicking "Remove Flag" below will remove your flag, thus reducing the count by one as well.

## I am deleting this answer because...

ABB Technical Guides - Motor Operation

ABB has produced a range of technical guides that offer concise explanations of the major technologies and technical issues in low voltage AC drives. ...

Electromagnetic Compatibility (EMC)

Electromagnetic compatibility (EMC) is the study of coordinating electromagnetic fields give off equipment, with the withstand (compatibility) of other...

Closed Doors

"I can live with doubt and uncertainty and not knowing. I think it is much more interesting to live not knowing than to have answers that might be wrong...

Maximum Demand for Buildings

Estimating maximum demand is a topic frequently discussed. Working out how much power to allow for a building can be very subjective . Allowing too much...

Motor Efficiency Classification

Electric motors are one of the most widely used items of electrical equipment. Improving motor efficiency benefits include, reduced power demand, lower...

Generator Sizing & Operation Limits

When selecting a generator, there are inherent limits on the active and reactive power which can be delivered. Generators are normally sized for a certain...

Lithium Ion Battery

Over recent years the Lithium Ion battery has become popular in applications requiring high power densities with small weight and footprint.  Today Lithium...

Hazardous Areas – IEC and NEC/CEC Comparison

Depending where in the world you work, you are likely following one of two standards International Electrotechnical Commission (IEC) National...

What does N+1 mean?

The term 'N+1' relates to redundancy and simply means that if you required 'N' items of equipment for something to work, you would have one additional...

Contribute to myElectrcial

Have an opinion or something to say, want to ask or answer questions, share your knowledge then use our site to do it . As a community of people interested...

Our website uses cookies so that we can provide a better experience.