# Transformer Impedance Calculation

 Hi all, I have a very fundamental question to ask. To compute a 3 phase fault current of a circuit supplied by a 1MVA transformer 22kV/ 400V with 5% impedance without using PU method, I understand it goes: TF impedance = 5% x 400^2/ 1x10^6 = 0.0084 ohm The 3 phase fault current per phase = 400/ 1.732/ 0.0084= 27.5kA I am puzzled by the TF impedance calculation.. why is there no 1.732 factor as with all 3 phase power calculations in this instance? Sorry for the very layman question asked here. But am really confused. Thanks. asked 5/26/2018 Fbearn2

 kVA / Voltage x 1.73 / TX Z%1000 / 400 x 1.73 / 5% = 28,9 kA answered 4 months ago Paddy Keys 3

In order to provide an answer to this question, you must Login

## I am flagging this question because...

10 inform moderator flags remaining

## I am flagging this answer because...

10 inform moderator flags remaining

## Flagging a Post

You have already flagged this post. Clicking "Remove Flag" below will remove your flag, thus reducing the count by one as well.

## I am deleting this answer because...

Years ago I was told that you should always try to write the best report you can.  Many years later I still think on this as one of the better pieces of...

Electric Motors

Collection of links to various places with useful motor information. I’ll try and return to the page every now and again to update it with any motor notes...

Motor Insulation

Insulation on a motor prevents interconnection of windings and the winding to earth.  When looking at motors, it is important to understand how the insulation...

Standard Cable & Wire Sizes

IEC 60228 is the International Electrotechnical Commission's international standard on conductors of insulated cables. Among other things, it defines a...

Photovoltaic (PV) Panel - Performance Modelling

In an earlier note on the site [Photovoltaic (PV) - Electrical Calculations], the theory of solar (PV) cell calculations was introduced.  In particular...

Paths of Flight

GE have put together a time-lapse video shown flight take-off and landings at some airports. An interesting view:

IEC 60287 Current Capacity of Cables - Rated Current

In the previous note we looked at the approach taken by the standard to the sizing of cables and illustrated this with an example.  We then looked at one...

What is Aircraft Ground Power

Ever wondered what kind of power an aircraft uses when parked at the airport stand. Normally the aircraft generates it own power, but when parked with...

9 power supply issues solved by using a UPS

Installation of a UPS can help in reducing problems due to issues with the power supply.  A lot of people relate this to nine key issues.  Depending on...

Understanding Motor Duty Rating

One of the comments on my Motor Starting Series was asking for something on duty cycles. Here it is. As a purchaser of a motor, you have responsibility...

Our website uses cookies so that we can provide a better experience.