# Transformer Impedance Calculation

 Hi all, I have a very fundamental question to ask. To compute a 3 phase fault current of a circuit supplied by a 1MVA transformer 22kV/ 400V with 5% impedance without using PU method, I understand it goes: TF impedance = 5% x 400^2/ 1x10^6 = 0.0084 ohm The 3 phase fault current per phase = 400/ 1.732/ 0.0084= 27.5kA I am puzzled by the TF impedance calculation.. why is there no 1.732 factor as with all 3 phase power calculations in this instance? Sorry for the very layman question asked here. But am really confused. Thanks. asked 5/26/2018 Fbearn2

 kVA / Voltage x 1.73 / TX Z%1000 / 400 x 1.73 / 5% = 28,9 kA answered 4 months ago Paddy Keys 3

In order to provide an answer to this question, you must Login

## I am flagging this question because...

10 inform moderator flags remaining

## I am flagging this answer because...

10 inform moderator flags remaining

## Flagging a Post

You have already flagged this post. Clicking "Remove Flag" below will remove your flag, thus reducing the count by one as well.

## I am deleting this answer because...

How to Size Power Cable Duct

Some colleagues had an issue earlier in the week on sizing conduits to be cast in concrete for some power cables . It became clear that none of us had...

Load Flow Study – how they work

A load flow study is the analysis of an electrical network carried out by an electrical engineer. The purpose is to understand how power flows around...

Understanding electric motor insulation & temperature

Anyone specifying or using electric motors should have a basic understanding how the insulation is related to temperature. Three classes of insulation...

Cables for MV Power Distribution - Earthed versus Unearthed Systems

Power cables can basically be classified into earthed and unearthed cables, where earthed and unearthed refer to the application for which the cable is...

Periodic Electrical Installation Inspection – What to Inspect?

This is the second post in a series of two on periodic electrical inspections. In the first post, I discussed how often inspections should be carried out...

DC Motor Operation

Coils of wire on the rotor carry a d.c. current which generates a magnetic field. A stator magnetic field is created using either permanent magnets or...

Introduction to Current Transformers

Current transformers (CTs) are used to convert high level currents to a smaller more reasonable level for use as inputs to protection relays and metering...

Maxwell's Equations - Gauss's Electric Field Law

Gauss's Electrical law defines the relation between charge ("Positive" & "Negative") and electric field.  The law was initially formulated by Carl Friedrich...

Occam's Razor

I was reminded of Occam's Razor while reading a book. It's quite a simple principal of logic which has stood the test of time and is accepted as central...

New Mail Chimp

We've been sending out Newsletters on a regular basis for a few weeks now. To do this we have been using Google's Feedburner service. While Feedburner...

Our website uses cookies so that we can provide a better experience.