## Cable Sizing Application

### What Changed

So that we can focus all our efforts on our new application, we have retired our myElectrical.com cable sizing calculator. We recommend you now use our main cable sizing application over at myCableEngineering.com.

### myCableEngineering.com

Cable Sizing Software - select, size and manage your power cables using myCableEngineering. All your cables, for all your projects.
• LV and MV cables up to 33 kV with current capacity in accordance with BS 7671, ERA 69-30 and IEC 60502.
• Positive and zero sequence impedance to IEC 60609. Voltage drop in accordance with CENELEC CLC/TR 50480.
• Project management and team collaboration, with clear easy to read calculations and reports.

Our software is the only cloud-based solution and has been built from the ground up to be fully responsive - meaning you can access your cables from anywhere and on any device, desktop, tablet or smartphone.

# Duct Size Calculator

Tip: registered users can save calculations.

### Typical Cable Diameters

Following outside diameters are for reference only and will vary depending on cable manufacturer.

600/1000V XLPE Armoured

Overall Diameter (mm)
mm2 1core  2 core  3 core  4 core
1.5    12.3  12.8  13.5
2.5    13.6  14.1  15.0
4    14.7  15.3  16.4
6    16.9  16.6  18.7
10    18.0  19.5  21.1
16     20.0  21.2  22.9
25    24.1  26.7  28.9
35    27.9  29.6  32.1
50*   17.5  25.8  28.5  32.0
70   20.2  29.0  32.2  37.7
95   22.3  33.1  37.0  41.7
120   24.2  36.1  40.0  47.7
150   27.4  39.3  45.5  51.4
185  30.0  44.7  49.8  56.6
240  32.8  49.0  55.1  63.0
300  35.6  53.5  60.2  68.8
400  40.4  59.0  66.6  78.1
500  44.2
630  48.8
800  55.4
1000  60.6

* - change in class of conductor

### Calculation

1. Required fill factor k (in decimal)
2. Cable diameter d, giving a cable area, a:

$a=\frac{\pi }{4}{d}^{2}$
3. Cable total area Ca = sum of area for all cables
4. Minimum duct diameter D:

$D=\sqrt{\frac{4{C}_{a}}{\pi k}}$

Random Numbers

Using laser optical pulses the random number generator utilizes the time between arrival of random photos to generate the numbers, ensuring true accuracy...

Electric Motors

Collection of links to various places with useful motor information. I’ll try and return to the page every now and again to update it with any motor notes...

Voltage Levels to IEC 60038

The standard aims to consolidate AC and traction voltages within the industry and defines the following bands: band 1 - A.C. systems 100 V to 1...

MIT OpenCourseWare

MIT OpenCourseWare, makes the materials used in teaching all MIT subjects available on the Web, free of charge, to any user in the world.

Nikola Tesla

Nikola Tesla was born exactly at midnight on July 10, 1856 in the tiny village of Smiljan, Lika in Croatia. In his late teens, Tesla left the village to...

UPS Sizing - Rules of Thumb

It wasn't so long ago I was telling someone that I don't use rules of thumb as most things are easily calculated anyhow.   As it turns out I last week...

A mechanical engineering paper, some history and memories

I was digging in my bookshelf and came across the 80th Anniversary Association of Mine Resident Engineers, Papers and Discussions Commemorative Edition...

1,000 kV UHV First for China

At the beginning of the year China put the world's first 1,000 kV UHV transmission system into operation. Transmitting power at over a million volts is...

How to refer fault levels across a transformer

Over the past year or so I've been involved in on going discussions related to referring fault levels from the secondary of a transformer to the primary...

International System of Units (SI System)

The International System of Units (abbreviated SI) is the world's most widely used system of units.  The system consists of a set of units and prefixes...

Our website uses cookies so that we can provide a better experience.