# Earth Electrode Resistance

By on May 17th, 2012

Earthing of electrical systems is essential for the correct functioning and the protecting of life and equipment in the event of faults. The earth electrode (connection of the earthing system to the ground) is an essential part of any system.

The estimation of electrode resistance and functioning during the design stage ensures workable solutions are proposed, enhances the operation and potentially reduces the cost of any installation.

## General Calculation of Electrode Resistance

Theoretical Example

Sphere of radius r, fully surrounded:

Method  - assume a current I, is injected into an electrode then at some point distant from the electrode, the current density is:

If the resistivity of the ground is r, the electric field is:

By integrating the electric field from the surface of the electrode to infinity, the voltage of the electrode is:

Apparent resistance Rg, can now be found from:

## Resistance and Distance from an Electrode

Resistance Contribution v's Distance
Around an earth electrode the resistance of the soil is the sum of series resistances of virtual shells of earth propagating outward from the electrode. Shells nearest to the electrode have the smallest surface area and hence the largest resistance.

The figure illustrates the contribution of the earth to the total resistance of the electrode at increasing distances from the surface of the electrode. As can be seen from the figure, 67% of the total resistance is accounted for at a distance of 0.3 M from the electrode.

In high resistivity locations, decreasing the resistivity in the area close to the electrode by use of ground enhancing materials  (chemical treatment or the use of concrete) will improve the effectiveness of the earth system.

## Resistance to Ground (Earth)

The following formula (source: IEEE Std.142:1991) enable the resistance to ground to be calculated.

 Hemisphere, radius a One ground rod, length L, radius a Two ground rods, s > L, spacing s Two ground rods, S < L, spacing s Buried horizontal wire, length 2L, depth s/2 Right angle turn of wire, length of arm L, depth s/2 Three point star, length of arm K, depth s/2 Four point star, length of arm L, depth s/2 Six point star, length of arm L, depth s/2 Eight point star, length of arm L, depth s/2 Ring of wire, diameter of ring D, diameter of wire d, depth s/2 Buried horizontal strip, length 2L, section a by b, depth s/2, B < a/8 Buried horizontal round plate, radius a, depth s/2 Buried vertical round plate, radius a, depth s/2

Where:
R - resistance in Ω
ρ - resistivity in Ω.cm
d - distances - in cm

## Multiple Ground Rods

Spacing Factor
No.Rods F
2 1.16
3 1.29
4 1.36
8 1.68
12 1.80
16 1.92
20 2.00
24 2.16

Spaced several rod lengths apart:

Spaced one rod length apart:

## Ground Enhancing Materials

Ground enhancing materials (GEM) is a technique where the ground immediately surrounding an earth electrode is replaced with a low resistance material. The intent is to reduce the earth electrode resistivity. Use of GEM would be in areas where the ground resistivity is very high and problems arise in trying to achieve the required electrode resistance.

## Calculation of Resistance

The resistance, R, expressed in ohms , of a vertical electrode surrounded by an infill of material
is given approximately by the following equation[2]:

Given:
ρ       - resistivity of soil (Ω.m)
ρc     - resistivity of infill material (Ω·m)
d       - diameter of electrode (m)
D       - diameter of infill (m)
L       - length of electrode (m)

### Issues and Concerns

GEM treatment may not be permanent and should be check regularly. This is particularly true of chemical treatment which may leach away into the surrounding soil over time resulting in the earth electrode resistance increasing to unacceptable levels. Some GEM treatments may also have corrosive effects on the earth electrode or other negative environmental consequences.

## References

• [1] IEE Std. 142-1991, Grounding of Industrial and Commercial Power Systems, Institute of Electrical and Electronic Engineers
• [2] BS 7430:1998, Code of Practice for Earthing, British Standards Institute

More interesting Notes:

Steven has over twenty five years experience working on some of the largest construction projects. He has a deep technical understanding of electrical engineering and is keen to share this knowledge. About the author

#### View 1 Comments (old system)

1. Joe says:
7/11/2012 5:13 PM

How would you approximate resistance if you had a four point star but, two ends of the star had ground rods connected?

Comments are closed for this post:
• have a question or need help, please use our Questions Section
• spotted an error or have additional info that you think should be in this post, feel free to Contact Us

## Latest Questions:

### Most Popular Notes:

Renewable and Efficient Electric Power ...
Gilbert M. Masters
Hardcover - 712 pages
$101.50 Solar Electricity Handbook - 2015 Edition: ... Michael Boxwell Paperback - 204 pages$17.09
Electric Power Distribution Engineering, ...
Turan Gonen
Hardcover - 1061 pages
$104.97 Energy Systems Engineering: Evaluation and ... Francis Vanek, Louis ... Hardcover - 672 pages$51.30
Power System Relaying
Stanley H. Horowitz, ...
Hardcover - 398 pages
$122.30 Renewable Energy in Power Systems Leon Freris, David ... Hardcover - 300 pages$67.20
Electric Energy: An Introduction, Third ...
Mohamed A. El-Sharkawi
Hardcover - 606 pages
$101.41 Photovoltaic Systems Engineering, Third ... Roger Messenger, Amir ... Hardcover - 528 pages$103.66
Photovoltaic Design and Installation For ...
Ryan Mayfield
Paperback - 384 pages
$16.99 Solar Engineering of Thermal Processes John A. Duffie, ... Hardcover - 936 pages$108.50
Design of Smart Power Grid Renewable Energy ...
Ali Keyhani
Hardcover - 592 pages
$142.06 Power Systems and Renewable Energy: Design, ... Gary D. Price Paperback - 192 pages$59.95
Power Electronics and Renewable Energy ...
Hardcover - 1607 pages
$399.00 Renewable and Efficient Electric Power ... Gilbert M. Masters Hardcover - 680 pages Solar PV Engineering and Installation: ... Sean White Paperback - 248 pages$37.27
Photovoltaics: Design and Installation ...
Solar Energy ...
Paperback - 336 pages
$38.12 Do It Yourself 12 Volt Solar Power, 2nd ... Michael Daniek Paperback - 128 pages$13.70
Solar Energy Engineering, Second Edition: ...
Soteris A. Kalogirou
Hardcover - 840 pages
$99.96 Electric Power Substations Engineering, ... Hardcover - 536 pages$149.95
Wind Turbine Operation in Electric Power ...
Zbigniew Lubosny
Paperback - 262 pages
$209.00 Submarine Power Cables: Design, ... Thomas Worzyk Hardcover - 296 pages$189.00
Alternative Energy Systems and Applications
B. K. Hodge
Paperback - 432 pages
Power Conversion and Control of Wind Energy ...
Bin Wu, Yongqiang ...
Hardcover - 480 pages
$86.35 Principles of Sustainable Energy Systems, ... Frank Kreith, Susan ... Hardcover - 790 pages$114.16
Smart Power Grids 2011 (Power Systems)
Hardcover - 696 pages
$299.00 Large-Scale Solar Power Systems: ... Dr Peter Gevorkian Paperback - 400 pages$72.74
Electrical Power System Essentials
Pieter Schavemaker, ...
Hardcover - 340 pages
$79.68 The Homeowner's DIY Guide to Electrical ... David Herres Paperback - 336 pages$25.00
Convex Optimization of Power Systems