# The dc resistance of conductors

By on

This is the first of two posts on the resistance of conductors.  In the next post I will look at the ac resistance, including skin effect and show how we can deal with this.  To get started, this post will look at the simpler case of dc resistance and how it can be calculated.

## DC Resistance to IEC 60287

The international standard for conductors is IEC 60287.  The standard classifies conductors according to four classes:

- Class 1: solid conductors

- Class 2: stranded conductors

- Class 5: flexible conductors

- Class 6: flexible conductors (more flexible than class 5)

For each class of conductor, the standard defines the maximum allowable resistance at 20 oC:

Minimum Resistance of Conductors in mΩ/m
CSA mm² Copper (plain) Copper (tinned) Aluminium
class 1 & 2 class 5 & 6 class 5 & 6 class 1 & 2
0.5 36.0 39.0 40.1 -
0.75 24.5 26.0 26.7 -
1 18.1 19.5 20.0 -
1.5 12.1 13.3 13.7 -
2.5 7.41 7.98 8.21 -
4 4.61 4.95 5.09 -
6 3.08 3.30 3.39 -
10 1.83 1.91 1.95 3.08
16 1.15 1.21 1.24 1.91
25 0.272 0.78 0.795 1.20
35 0.524 0.554 0.565 0.868
50 0.387 0.386 0.393 0.641
70 0.268 0.272 0.277 0.443
95 0.193 0.206 0.210 0.320
120 0.153 0.161 0.164 0.253
150 0.124 0.129 0.132 0.206
185 0.0991 0.106 0.108 0.164
240 0.0754 0.0801 0.0817 0.125
300 0.0601 0.0641 0.0654 0.100
400 0.0470 0.0486 0.0495 0.0778
500 0.0366 0.0384 0.0391 0.0605
630 0.0283 0.0287 0.0292 0.0469
800 - - - 0.0367
1000 - - - 0.0291
1200 - - - 0.0247

## DC Resistance - calculation

For solid conductors the resistance (theoretically) can also be calculated using the standard formula:

If the length (l) is in metres, cross sectional area, a in m2 (mm2 x10-6) and resistivity ρ in Ω-m, then the Resistance will be in ohms. The resistivity in Ω-m (at 20 oC) for copper is 1.72x10-8 and for aluminium 2.82x10-8.

The above formulae does not take into account manufacturing tolerances, compactness of stranded conductors, etc.  These will result in the calculated resistance differing from any actual measured resistance.  For general use it is probably better to use the figures from the IEC 60287 table, rather than calculation using the above formula.

## Temperature dependence

The above values of resistance are based on a temperature of 20 oC.  Resistivity of the conductor will varies with temperature, with the resistance increasing as temperature increases.  This variation can be simplified to a linear function for a reasonable temperature range as follows:

• R      = the resistance of the conductor at temperature T
• R20   = conductor resistance at 20 oC
• T      = operating temperature of the conductor
• α      = temperature coefficient of resistivity

Actual values of α, depend on the composition of the material in addition to the temperature. For both copper and aluminium, α taken as 0.0039 will give sufficient accuracy for most conductor calculations.

The ac resistance of conductors ->

More interesting Notes:

Steven has over twenty five years experience working on some of the largest construction projects. He has a deep technical understanding of electrical engineering and is keen to share this knowledge. About the author

myElectrical Engineering

#### View 1 Comments (old system)

1. Notes says:
2/1/2013 10:30 AM

IEC 60287 "Calculation of the continuous current rating of cables (100% load factor)" is the International Standard which defines the procedures and equations to be used in determining the current carry capacity of cable. The standard is applicable... ...

Comments are closed for this post:
• have a question or need help, please use our Questions Section
• spotted an error or have additional info that you think should be in this post, feel free to Contact Us

8 Motor parts and common faults

Straight forward list of some common motor faults.  If I have missed any other common faults, please take a bit of time to add them in as a comment below...

UPS Sizing - Rules of Thumb

It wasn't so long ago I was telling someone that I don't use rules of thumb as most things are easily calculated anyhow.   As it turns out I last week...

ABB Technical Guides - Motor Operation

ABB has produced a range of technical guides that offer concise explanations of the major technologies and technical issues in low voltage AC drives. ...

Star-Delta Motor Starting - Performance

Many questions sent in to the site are in connection with motor starting and in particular star-delta.  For all but the simplest application, there is...

Wiki Depreciation

We have had the Wiki with us for a long time now, but at last I have decided to say bye bye – more details on why below.

1,000 kV UHV First for China

At the beginning of the year China put the world's first 1,000 kV UHV transmission system into operation. Transmitting power at over a million volts is...

Cable Sheath and Armour Loss

When sizing cables, the heat generated  by losses within any sheath or armour need to be evaluated. When significant, it becomes a factor to be considered...

A mechanical engineering paper, some history and memories

I was digging in my bookshelf and came across the 80th Anniversary Association of Mine Resident Engineers, Papers and Discussions Commemorative Edition...

Robots - Interesting Videos

The robot folding towels post below was interesting enough at the time to post a link.  Recently I’ve come across a couple of other interesting videos...

myElectrical - Cable Sizing Tool Upgrade

Our IEE cable sizing was wrote a few years ago and had become rough around the edges. I thought it was time to give the tool a service. Unfortunately when...

## Have some knowledge to share

If you have some expert knowledge or experience, why not consider sharing this with our community.

By writing an electrical note, you will be educating our users and at the same time promoting your expertise within the engineering community.

To get started and understand our policy, you can read our How to Write an Electrical Note