# Electromagnetic Compatibility (EMC)

By on July 10th, 2012

CE Mark Layout

Electromagnetic compatibility (EMC) is the study of coordinating electromagnetic fields give off equipment, with the withstand (compatibility) of other equipment within the vicinity. In it's simplest form, we endeavour to ensure that the magnitude of any electromagnetic fields generated are less than the withstand level of adjacent equipment.

Within Europe there is the EMC directive (2004/108/EC), which is law in all European Countries.  Equipment which bears the CE mark has been certified to comply with the relevant standards.

## How EMC Works

Electrical equipment which generate eclectic and magnetic fields are called sources of electromagnetic (EM) interference.  Differing types of equipment generate different levels of EM; for example a large transmission line will generate a high level of EM, while a pocket calculation will not generator much.

How EMC Works

By its nature, EM can and will interfere with the correct operation of equipment.  How severely it interferes with the equipment depends on its sensitivity to EM interference and the magnitude of the EM. Equipment which absorb and are affected by EM are called sinks.  For most sinks there is an immunity level, which if the magnitude of the EM interference is below this it will not affect the equipment

Typical Interference Producers

- switching of main and secondary circuits
- lightning strokes and induced discharges
- operation of surge arrestors and air gaps
- radio and mobile phone transmitters
- short circuits and earth faults
- equipment electromagnetic fields
- electrostatic discharges

Common Mitigation Measures

- protection measures for lightning
- adequate earthing and bonding
- separation of power and control cables
- shielding  and earthing of control cables
- avoid loops (keep send/return conductors together)

EM interference needs to moves from the source to the sink by some form of coupling.  These take the form of:

Electrostatic coupling - discharge of charged bodies

Inductive coupling - via magnetic fields

Capacitive coupling - via electric fields

Conductive (galvanic) coupling - via circuit impedances

Radiation - EM propagation where structure dimensions large compared to wavelength

In system design, the aim of achieving EMC compliance is to to ensure that the EM interference generated by all the sources is less than the EM immunity levels for each of the sinks.

In general this is achieved by limiting the penetration of fields (screens for example) and ensuring a equipotential plane between equipment.

## EMC Standards

When trying to ensure or verify EMC the base international standard is IEC 6100.  The standard consists of compliance requirements, collected data and guidelines:

• IEC 61000 Electromagnetic compatibility (EMC) -
• Part 1: General - 6 parts on application and methodology
• Part 2: Environment - 14 parts on compatibility levels, assessment and environments
• Part 3: Limits - 15 parts on the emissions and disturbances for various systems
• Part 4: Testing and measurement techniques - 35 parts covering emission and immunity testing
• Part 5: Installation and mitigation guidelines - 9 parts cover installation requirements
• Part 6-1: Generic standards - 6 parts on specifics for residential, industrial and commercial environments

In addition to the IEC 61000, particular items of equipment will likely have additional EMC requirements built into the product standard itself. Industries and special environments could also have their own EMC standards; for example rail systems would be required to adhere to  IEC 62236 and EN 50121 "Railway applications - Electromagnetic compatibility".

Note: electromagnetic fields can also have an adverse effect on human health.  The International Commission on Non-Ionizing Radiation Protection (ICNIRP) publishes research and guidelines on recommended exposure limits for electromagnetic fields.  You can visit their website at: http://www.icnirp.de.

## Implementation in Installations

Determining the level of EMC for an installation essentially involves looking at all the sources of EM and comparing these to the immunity level of the sinks.  For many installations this is relatively straightforward as the individual product standards, will be default guarantee  For some installations it would also involve the system as a whole, its EM emissions and the effect on the neighbouring environment.

### EMC Management Plan

For large installations and systems, it would be good practice to develop and EMC management plan. The EMC plan would establish the goals for the system EMC compliance and show how this will be achieved.  A typical EMC plan may include some of all of the following:

• Identification of the likely sources of interference
• Listing EMC regulations, customer specifications, standards, in-house specifications
• EMC management rationale
• Responsibilities of the consultant, contractor and suppliers
• Control of suppliers - possibly with suppliers own EMC plans
• Whole system EMC management
• Deliverable documentation
• Time management - milestones, testing, etc.
• Compliance Matrix documenting  each system, subsystem or equipment as both a source and sink
• Test Matrix

### Earthing and Bonding

Over and above the product selection, the primary method used to achieve EMC compliance goals for most installations is the earthing and boding.  Particular care should be given to this and it would be worthwhile developing guidelines to be followed for the installation as a whole.   Some general earthing and bonding tactics to improve EMC include:

• earthing of the enclosures of EM generating equipment
• compliance with relevant earthing installation standards
• utilising clean earth and intrinsically safe earth systems as appropriate
• multiple earth-bonding utilising meshed earths
• create large numbers of small earth loops
• avoiding star earthing and/or the provision of separate earths for protective and clean
• provide an earth plane for each floor (mesh or reinforcing or copper)
• keep bonding connections as short as possible (and of low resistance and inductance)
• ensure the earthing and bonding is resistant to corrosion, shock and vibration
• cable screens and armour should be earth bonded at the point of entry to enclosures

### Cables

Cables are both sources of EM and a distribution path.  Ensuring the correct selection and installation will help minimise any EM problems.  In particular it would be worthwhile ensuring:

• bonding at all ends for metallic cable trays, flexible metallic tubes and steel pipes
• bonding of cable shields at both ends
• run single core cables of the same  power circuit together
• use screens or armour with multi-core cables
• apply surge arrestor and filter at the incoming to switchgear panels
• special separation of cables:
• communication/data cables > 300 mm from low voltage cables (60 V to 1 kV)
• communication/data/low voltage cables > 600 mm from high voltage cables (>1 kV)

### Particular Items

Particular items of equipment will more prone to creating EM issues or being affected by them.  Obvious examples of EM generating equipment would where large amounts of power are used, larger inverters and other large non-linear power users.   Sensitive equipment examples would include rail signalling, control or communications systems or other low power devices.

Finally to ensure full compliance, it may be required to conduct field survey of the installations neighbourhood and carryout an appropriate level to testing and verification.

## Summary

Electromagnetic compliance (EMC) is the design and installation of equipment and systems, such that the electromagnetic fields generated by the equipment does not affect other adjacent equipment or systems.   Achieving EMC compliance is primarily governed by IEC 61000.  For any large installation, the production of an EMC management plan will assist in ensuring compliance during design, installation and operation.

As always, if you have any comments or discussion on the post, please add below.

More interesting Notes:

Steven has over twenty five years experience working on some of the largest construction projects. He has a deep technical understanding of electrical engineering and is keen to share this knowledge. About the author

#### View 6 Comments (old system)

1. ram31 says:
7/1/2013 1:10 AM

Do electrical and low current devices/equipments in railway/metro/tram stations areas have to comply with EN 50121 series and comply with IEC 61000 series in non-railway areas?

• Steven says:
7/1/2013 8:36 AM

I think that in principal you are correct. How to apply this is debatable.

EN 50121 appears to say emissions should be considerable to exist within 10 m of the centreline of tacks or substation fence. Part 4, gives guidance on signalling and telecommunication equipment within 3 m of the centreline.

On one project I've been involved with, the following practice was adopted:

* 10 and 3 metre zones defined from track centreline or overhead conductor
* any electronic, control type equipment within the 3 m zone to comply with EN 50121
* any safety related equipment within the 10 m zone to EN 50121
* other electronic, control equipment within the 10 m zone to 61000, industrial environment
* equipment outside the 10 m zone to 61000, residential, commercial & light industrial environment

Hope this helps.

• ram31 says:
7/2/2013 3:15 AM

Can you please guide in which category the following Electrical & ELV devices used in buildings will be categorized as per the definitions ( control and safety)shown in your reply -
1.Light fixtures & sources
2 .small power devices(switch sockets,connection units,spur outlets,flex outlets)
3. Cameras
4. Access control(card readers,push buttons)
5. Fire alarm devices (smoke,heat, manual call point,strobe,sounder)
6. Voice evacuation devices( ceiling and wall speakers)

1.Lighting manufacturers(Philips,Thorn) are stating that EN 50121 are not applicable for their products and there are no light fixtures available which comply with EN 50121.They are complying with EN 61000-3-2 & EN 61000-3-3.

• Steven says:
7/2/2013 8:45 AM

It is difficult to comment, as each project is approached differently. All the devices you list could possibly be fine with just the 61000 standard.

To be safe you may want to look at the immunity levels of anything electronic and make a judgment call as to whether this is fine or not. Particularly if it is safety related.

2. ram31 says:
7/20/2013 12:15 PM

A).Can you please state the exact 61000 standard which the above mentioned devices have to comply among the following listed below-
1. 61000-6-1,61000-6-2,61000-6-3,61000-6-4
2. 61000-3-2 ,61000-3-3

B).What should be the required immunity level for safety related equipments?

3. ram31 says:
7/21/2013 12:58 AM

In my project the light fixtures are complying with
a.) EN 610000-3-2 -EMC for Harmonic current emisssion
b.) EN 61000-3-3 - EMC for voltage flucations and flicker
c) EN 55015 EMC radio disturbance characteristics
d) EN 61547 EMC for immunity

Are these compliances sufficient for the EMC requirements?

Comments are closed for this post:
• have a question or need help, please use our Questions Section
• spotted an error or have additional info that you think should be in this post, feel free to Contact Us

## Latest Questions:

### Most Popular Notes:

Solar Electricity Handbook - 2015 Edition: ...
Michael Boxwell
Paperback - 204 pages
$16.96 Electric Power Distribution Engineering, ... Turan Gonen Hardcover - 1061 pages$137.08
How to Solar Power Your Home Everything You ...
Martha Maeda
Paperback - 336 pages
$14.99 Power System Relaying Stanley H. Horowitz, ... Hardcover - 398 pages$122.30
Electric Energy: An Introduction, Third ...
Mohamed A. El-Sharkawi
Hardcover - 606 pages
$103.86 Power Electronics and Renewable Energy ... Hardcover - 1607 pages$225.29
Submarine Power Cables: Design, ...
Thomas Worzyk
Hardcover - 296 pages
$189.00 Power Quality in Power Systems and ... Ewald Fuchs, Mohammad ... Hardcover - 800 pages$150.00
Renewable Energy in Power Systems
Leon Freris, David ...
Hardcover - 300 pages
$86.40 The Homeowner's DIY Guide to Electrical ... David Herres Paperback - 336 pages$19.08
Large-Scale Solar Power Systems: ...
Dr Peter Gevorkian
Paperback - 400 pages
$49.99 Photovoltaic Systems Engineering, Third ... Roger A. Messenger, ... Hardcover - 528 pages$103.59
Solar PV Engineering and Installation: ...
Sean White
Paperback - 296 pages
$36.89 Energy Systems Engineering: Evaluation and ... Francis Vanek, Louis ... Hardcover - 672 pages$60.99
Renewable and Efficient Electric Power ...
Gilbert M. Masters
Hardcover - 712 pages
$105.25 Large-Scale Solar Power System Design ... Peter Gevorkian Hardcover - 704 pages$98.33
Convex Optimization of Power Systems
Hardcover - 209 pages
$90.77 Photovoltaics: Design and Installation ... Solar Energy ... Paperback - 336 pages$37.05
Alternative Energy Systems and Applications
B. K. Hodge
Paperback - 432 pages
Wind Turbine Operation in Electric Power ...
Zbigniew Lubosny
Paperback - 262 pages
$209.00 Smart Power Grids 2011 (Power Systems) Hardcover - 696 pages$299.00
Principles of Sustainable Energy Systems, ...
Frank Kreith, Susan ...
Hardcover - 790 pages
$112.94 Renewable Fuel Standard:: Potential ... Committee on Economic ... Paperback - 250 pages$68.00
Grid Converters for Photovoltaic and Wind ...
Remus Teodorescu, ...
Hardcover - 416 pages
$111.77 Solar Electricity Handbook - 2012 Edition: ... Michael Boxwell Paperback - 200 pages Electric Power Substations Engineering, ... Hardcover - 536 pages$125.96
Do It Yourself 12 Volt Solar Power, 2nd ...
Michael Daniek
Paperback - 128 pages
$12.86 Solar Engineering of Thermal Processes John A. Duffie, ... Hardcover - 936 pages$99.04
Electric Power Distribution System ...
Turan Gonen
Hardcover - 856 pages

## Have some knowledge to share

If you have some expert knowledge or experience, why not consider sharing this with our community.

By writing an electrical note, you will be educating our users and at the same time promoting your expertise within the engineering community.

To get started and understand our policy, you can read our How to Write an Electrical Note