# Arc Flash Calculations

By on

Arc Flash
Working in the vicinity of electrical equipment poses an hazard.  In addition to electric shock hazard, fault currents passing through air causes Arc Flash.

During arc flash, temperatures of 20,000 oC for several metres around equipment can exist, resulting in severe burn injuries.  Quickly expanding air and vaporization of metals causes high pressures, sound and shrapnel leading to multiple types of injuries.

To protect people a risk analysis on the arc flash hazard is carried out to better understand what may occur.  Appropriate procedures and personal protective equipment are then employed to minimise potential injuries.

When evaluating arc flash there are two main considerations, 1) the incident energy in the arc flash and 2) flash protection boundary.  I will be looking at the calculation of these two parameters in terms of IEE Std. 1584 'IEEE Guide for Performing Arc-Flash Hazard Calculations'.

## IEE 1584 Calculation Method

Symbols and their meaning:

V  -    system voltage (kV)
Ibf    -    bolted three phase fault current (kA)
Ia   -    arcing current (kA)
E   -    incident energy (J/cm2)
EB  - incident energy at boundary distance (J/cm2)
En  - normalized incident energy (J/cm2)
t    -    arcing time (s)
D   - distance from arc to person (mm)
CB  - distance of boundary from arc point (mm)

### Arcing Current

In order to determine both the flash protection boundary and incident energy, first the arcing current needs to be calculated.

For system voltages under 1000 V:

$log 10 ( I a )=K+0.662 log 10 ( I bf )+0.0966V+0.000526G+0.5588Vlo g 10 ( I bf )−0.00304 G log 10 ( I bf )$

Where:

K = -0.153 for open configurations and -0.097 for box configurations

For system voltages above 1000 V:

$log 10 ( I a )=0.00402+0.983 log 10 ( I bf )$

The arcing current is then given by:

$I a = 10 log 10 ( I a )$

### Incident Energy

To calculated the incident energy, first normalized incident energy is calculated.  The result of this calculation is the incident energy for a arc duration to 0.2 s and at a distance from the arc point to the person of 610 mm.  Once the normalized energy has been calculated, this is then adjusted to reflect the actual arcing time and distance.

The normalized incident energy is given by:

$log 10 ( E n )= K 1 + K 2 +1.081 log 0 ( I a )+0.0011G$

$E n = 10 log 10 ( E n )$

Where:

K1 = -0.792 for open configurations and -0.555 for boxed configurations

K2 = 0 for ungrounded or high resistance ground systems and -0.113 for grounded systems

G = the conductor gap (see table below)

The incident energy is then given by:

$E=4.184 C f E n ( t 0.2 )( 610 x D x )$    - voltages ≤ 15 kV and gaps ≤ 152 mm

Where:

Cf    = 1.0 for voltages greater than 1000 V and 1.5 for voltages less than 1000 V

x    = is a distance exponent from the table below

$E=2.142× 10 6 V I bf ( t D 2 )$ - voltages > 15 kV or gaps > 152mm

Note: for voltages greater than 15 kV, it is not necessary to first calculate En

Note: to convert J/cm2 to cal/cm2 multiply by 0.239

Gap and distance factors

Voltage (kV)

Equipment Type
Typical gap between
conductors (mm)
Distance factor,
x
0.208 - 1

Open Air 10-40 2.000
Switchgear 32 1.473
MCC and Panels 25 1.641
Cable 13 2.000
>1 - 5 Open Air 102 2.000
Switchgear 13-102 0.973
Cables 13 2.000
>5 -15 Open Air 13-153 2.000
Switchgear 153 0.973
Cables 13 2.000

### Flash Protection Boundary

The flash boundary is the distance from the arc point to a location when the incident energy is less than a given value.  Knowing the incident energy, the flash boundary distance is given by:

$D B = [ 4.184 C f E n ( t 0.2 )( 610 x E B ) ] 1 x$- voltages ≤ 15 kV and gaps ≤ 152 mm

$D B = 2.142× 10 6 V I bf ( t E B )$- voltages > 15 kV or gaps > 152 mm

Where:

Cf = 1.0 for voltages greater than 1000 V and 1.0 for voltages less than 1000 V

x = is a distance exponent from the table above

EB can be set at 5.0 J/cm2 for bare skin or at the rating of any proposed PPE.  The limit of 5.0 J/cm2 is that at which a person is likely to receive second degree burns.

### Summary

To carry out arc flash calculations, first workout the arcing current, then the incident energy and finally the arc flash boundary.  Pretty straight forward.

To make life a little easier I have created a calculator to do the grunt work.  You can find it here:

Arc Flash Calculator

It anyone has an comments or spots any errors in the above, please chip in below.

More interesting Notes:

Steven has over twenty five years experience working on some of the largest construction projects. He has a deep technical understanding of electrical engineering and is keen to share this knowledge. About the author

myElectrical Engineering

Mobile Phones (Brick to Implant)

The mobile phone was born in 1973. They were the size of a brick and weighed a couple of kg, making them difficult to fit into your pocket. At a few thousand...

UPS - Uninterruptible Power Supply

A UPS is an uninterruptible power supply.  It is a device which maintains a continuous supply of electrical power, even in the event of failure of the...

Wiki Depreciation

We have had the Wiki with us for a long time now, but at last I have decided to say bye bye – more details on why below.

Arc Flash Calculations

Working in the vicinity of electrical equipment poses an hazard. In addition to electric shock hazard, fault currents passing through air causes Arc Flash...

Tech Topics/Application Notes - Siemens

There are a lot of interesting two page type notes on various medium voltage topics – switchgear, circuit breakers, bus systems etc. It is on the Siemens...

Cable Sheath and Armour Loss

When sizing cables, the heat generated  by losses within any sheath or armour need to be evaluated. When significant, it becomes a factor to be considered...

A mechanical engineering paper, some history and memories

I was digging in my bookshelf and came across the 80th Anniversary Association of Mine Resident Engineers, Papers and Discussions Commemorative Edition...

Low Voltage Circuit Breakers

Circuit breakers are switching devices whose primary function is to isolate parts of an electrical distribution system in the even of abnormal conditions...

Cables for MV Power Distribution - Earthed versus Unearthed Systems

Power cables can basically be classified into earthed and unearthed cables, where earthed and unearthed refer to the application for which the cable is...