# Arc Flash Calculations

By on

Arc Flash
Working in the vicinity of electrical equipment poses an hazard.  In addition to electric shock hazard, fault currents passing through air causes Arc Flash.

During arc flash, temperatures of 20,000 oC for several metres around equipment can exist, resulting in severe burn injuries.  Quickly expanding air and vaporization of metals causes high pressures, sound and shrapnel leading to multiple types of injuries.

To protect people a risk analysis on the arc flash hazard is carried out to better understand what may occur.  Appropriate procedures and personal protective equipment are then employed to minimise potential injuries.

When evaluating arc flash there are two main considerations, 1) the incident energy in the arc flash and 2) flash protection boundary.  I will be looking at the calculation of these two parameters in terms of IEE Std. 1584 'IEEE Guide for Performing Arc-Flash Hazard Calculations'.

## IEE 1584 Calculation Method

Symbols and their meaning:

V  -    system voltage (kV)
Ibf    -    bolted three phase fault current (kA)
Ia   -    arcing current (kA)
E   -    incident energy (J/cm2)
EB  - incident energy at boundary distance (J/cm2)
En  - normalized incident energy (J/cm2)
t    -    arcing time (s)
D   - distance from arc to person (mm)
CB  - distance of boundary from arc point (mm)

### Arcing Current

In order to determine both the flash protection boundary and incident energy, first the arcing current needs to be calculated.

For system voltages under 1000 V:

$log 10 ( I a )=K+0.662 log 10 ( I bf )+0.0966V+0.000526G+0.5588Vlo g 10 ( I bf )−0.00304 G log 10 ( I bf )$

Where:

K = -0.153 for open configurations and -0.097 for box configurations

For system voltages above 1000 V:

$log 10 ( I a )=0.00402+0.983 log 10 ( I bf )$

The arcing current is then given by:

$I a = 10 log 10 ( I a )$

### Incident Energy

To calculated the incident energy, first normalized incident energy is calculated.  The result of this calculation is the incident energy for a arc duration to 0.2 s and at a distance from the arc point to the person of 610 mm.  Once the normalized energy has been calculated, this is then adjusted to reflect the actual arcing time and distance.

The normalized incident energy is given by:

$log 10 ( E n )= K 1 + K 2 +1.081 log 0 ( I a )+0.0011G$

$E n = 10 log 10 ( E n )$

Where:

K1 = -0.792 for open configurations and -0.555 for boxed configurations

K2 = 0 for ungrounded or high resistance ground systems and -0.113 for grounded systems

G = the conductor gap (see table below)

The incident energy is then given by:

$E=4.184 C f E n ( t 0.2 )( 610 x D x )$    - voltages ≤ 15 kV and gaps ≤ 152 mm

Where:

Cf    = 1.0 for voltages greater than 1000 V and 1.5 for voltages less than 1000 V

x    = is a distance exponent from the table below

$E=2.142× 10 6 V I bf ( t D 2 )$ - voltages > 15 kV or gaps > 152mm

Note: for voltages greater than 15 kV, it is not necessary to first calculate En

Note: to convert J/cm2 to cal/cm2 multiply by 0.239

Gap and distance factors

Voltage (kV)

Equipment Type
Typical gap between
conductors (mm)
Distance factor,
x
0.208 - 1

Open Air 10-40 2.000
Switchgear 32 1.473
MCC and Panels 25 1.641
Cable 13 2.000
>1 - 5 Open Air 102 2.000
Switchgear 13-102 0.973
Cables 13 2.000
>5 -15 Open Air 13-153 2.000
Switchgear 153 0.973
Cables 13 2.000

### Flash Protection Boundary

The flash boundary is the distance from the arc point to a location when the incident energy is less than a given value.  Knowing the incident energy, the flash boundary distance is given by:

$D B = [ 4.184 C f E n ( t 0.2 )( 610 x E B ) ] 1 x$- voltages ≤ 15 kV and gaps ≤ 152 mm

$D B = 2.142× 10 6 V I bf ( t E B )$- voltages > 15 kV or gaps > 152 mm

Where:

Cf = 1.0 for voltages greater than 1000 V and 1.0 for voltages less than 1000 V

x = is a distance exponent from the table above

EB can be set at 5.0 J/cm2 for bare skin or at the rating of any proposed PPE.  The limit of 5.0 J/cm2 is that at which a person is likely to receive second degree burns.

### Summary

To carry out arc flash calculations, first workout the arcing current, then the incident energy and finally the arc flash boundary.  Pretty straight forward.

To make life a little easier I have created a calculator to do the grunt work.  You can find it here:

Arc Flash Calculator

It anyone has an comments or spots any errors in the above, please chip in below.

More interesting Notes:

Steven has over twenty five years experience working on some of the largest construction projects. He has a deep technical understanding of electrical engineering and is keen to share this knowledge. About the author

myElectrical Engineering

The dc resistance of conductors

This is the first of two posts on the resistance of conductors. In the next post I will look at the ac resistance, including skin effect and we deal with...

110 or 230 Volts

I've been considering a blog on the 110 or 230 Volt issue for a while.  While browsing the Internet I came across a great summary by Borat over at  engineering...

Fault Calculations - Introduction

Fault calculations are one of the most common types of calculation carried out during the design and analysis of electrical systems. These calculations...

Inductance

When current flows within a wire, a magnetic field is created. The potion of this magnetic field perpendicular to the wire is called the magnetic flux...

What is LED?

Light Emitting Diodes (LED ) are increasing gaining favour in both the domestic and commercial sectors; due to their efficiency, sustainability and durability...

Differential protection, the good old days

This morning I was explaining how differential protection works to a junior engineer. To give him something to read I opened up the NPAG (Network Protection...

Photovoltaic (PV) Panel - Performance Modelling

In an earlier note on the site [Photovoltaic (PV) - Electrical Calculations], the theory of solar (PV) cell calculations was introduced.  In particular...

Material Properties

Everything physical in electrical engineering from insulations to conductors revolves around materials. Here we are listing common materials along with...

MIT OpenCourseWare

MIT OpenCourseWare, makes the materials used in teaching all MIT subjects available on the Web, free of charge, to any user in the world.

Questions - Reputation and Privilege

Our question and answer system while letting you do exactly what it says, is much more.  It is a dynamic user driven system, where our users not only ask...

## Have some knowledge to share

If you have some expert knowledge or experience, why not consider sharing this with our community.

By writing an electrical note, you will be educating our users and at the same time promoting your expertise within the engineering community.

To get started and understand our policy, you can read our How to Write an Electrical Note