# Fault Calculations - Typical Equipment Parameters

By on

A frequent problem in fault calculations is the obtaining of equipment parameters. While it is always preferable to use the actual parameters of the equipment, sometimes these are not available. In this instance it is necessary to resort to the use of typical parameters.

## HV Network Impedance

Impedance of HV network referred to LV side of transformer

 Psc Uo (V) Ra (mΩ) Xa (mΩ) 250 MVA 420 0.106 0.71 500 MVA 420 0.053 0.353

## Low Voltage Power Transformers

### Transformer Short Circuit Impedance

Typical values short circuit impedance, USC for different kVA ratings (HV winding < 20 kV)

 Type of Transformer transformer rating oil-immersed cast-resin 50 to 630 4% 6% 800 to 2500 6% 6%

### Transformer Impedance (400 V)

Resistance, reactance and impedance for typical transformers (HV winding <20 kV)

 transformer rated power (kVA) 50 100 160 250 315 400 500 630 800 1000 1250 1600 2000 2500 oil-immersed Usc % 4 4 4 4 4 4 4 4 6 6 6 6 6 6 Rtr mΩ 95.3 37.9 16.2 9.2 6.9 5.1 3.9 2.9 2.9 2.3 1.8 1.4 1.1 0.9 Xtr mΩ 104.1 59.5 41 26.7 21.3 16.9 13.6 10.8 12.9 10.3 8.3 6.5 5.2 4.1 Ztr mΩ 141.1 70.5 44.1 28.2 22.4 17.7 14.1 11.2 13.2 10.6 8.5 6.6 5.3 4.2 cast-resin Usc % 6 6 6 6 6 6 6 6 6 6 6 6 6 6 Rtr mΩ 33.5 18.6 10.7 8.2 6.1 4.6 3.5 2.6 1.9 1.5 1.1 0.8 0.6 Xtr mΩ 100.4 63.5 41 32.6 25.8 20.7 16.4 13 10.4 8.3 6.5 5.2 4.2 Ztr mΩ 105.8 66.2 42.4 33.6 26.5 21.2 16.8 13.3 10.6 8.4 6.6 5.3 4.2

## Synchronous Machines

### Performance Under Fault Conditions

Sub-transient emf:

Transient emf:

Synchronous emf:
Fault current:

## Typical Machine Reactances

Typical Machine Reactances (& Time Constants

 Cylindrical Rotor Turbine Generators Salient Pole Generators Salient Pole Synchronous Condensers Conventional Direct Cooled 4 Pole Multi-Pole Synchronous Direct axis Xd pu 1.6-2.0 0.8-1.0 2.0-2.3 2.1-2.4 1.3-2.1 1.3-1.5 Quadrature axis Xq pu 1.0-1.25 0.5-0.65 1.95-2.1 1.95-2.25 0.6-1.2 0.8-1.0 Transient Reactance Xd' pu 0.3-0.5 0.2-0.35 0.18-0.25 0.27-0.30 0.15-0.35 0.4-0.5 Short circuit τd' s 1.5-2.5 1.0-2.0 0.75-1.0 0.75-1.0 0.8-1.2 0.8-1.2 Open circuit τdo' s 5-10 3-7 4-8 6-9.5 4-8 3-7 Sub-transient Direct axis Xd'' pu 0.2-0.4 0.12-0.25 0.11-0.13 0.19-0.23 0.1-0.25 0.2-0.35 Quadrature axis Xq'' pu 0.25-0.6 0.15-0.45 0.11-0.13 0.19-0.23 0.14-0.35 0.2-0.35 Short circuit - direct axis τd' s 0.04-0.09 0.05-0.10 0.015-0.025 0.02-0.03 0.02-0.04 0.02-0.07 Open circuit - direct axis τd'' s 0.07-0.11 0.08-0.25 0.015-0.025 0.02-0.03 0.04-0.07 0.02-0.07 Short circuit - quadrature axis τq'' s 0.04-0.6 0.05-0.6 0.015-0.025 0.02-0.03 0.10-0.15 0.02-0.07 Open circuit - quadrature axis τq0'' s 0.1-1.2 0.2-0.9 0.015-0.025 0.02-0.03 0.3-0.7 0.1-0.2 Other Reactances Negative sequence X-ve pu 0.25-0.5 0.14-0.35 0.11-0.13 0.19-0.23 0.12-0.3 0.2-0.35 Zero sequence Xo pu 0.12-0.16 0.06-0.10 0.05-0.075 0.11-0.16 0.03-0.10 0.1-0.2

## Cables

where:

d = distance between centre
a = cross sectional area (mm)

More interesting Notes:

Steven has over twenty five years experience working on some of the largest construction projects. He has a deep technical understanding of electrical engineering and is keen to share this knowledge. About the author

myElectrical Engineering

Photovoltaic (PV) Panel - Performance Modelling

In an earlier note on the site [Photovoltaic (PV) - Electrical Calculations], the theory of solar (PV) cell calculations was introduced.  In particular...

Post Editing Tips

If you at all familiar with programs like office and outlook, then adding and editing posts is pretty straightforward and intuitive.  However, there are...

Arc Flash Calculations

Working in the vicinity of electrical equipment poses an hazard. In addition to electric shock hazard, fault currents passing through air causes Arc Flash...

IEC Reference Designations

The IEC publishes a series of documents and rules governing the preparation of documents, drawings and the referencing of equipment.   Depending on country...

Why a Sine Wave?

I received this question by email a few weeks. First thoughts was that it is a product of the mathematics of rotating a straight conductor in a magnetic...

How to Size Power Cable Duct

Some colleagues had an issue earlier in the week on sizing conduits to be cast in concrete for some power cables . It became clear that none of us had...

Occam's Razor

I was reminded of Occam's Razor while reading a book. It's quite a simple principal of logic which has stood the test of time and is accepted as central...

Lighting - Lamps

Lamps are the essential part of any luminaire. These are the light generating components. Since the advent of electrical lighting in the middle of the...

E-Ink

Before the technical, some general information. E-ink display are found in a lot of e-readers, some mobile phones and similar devices and the intent is...

Network Theory – Introduction and Review

In electrical engineering, Network Theory is the study of how to solve circuit problems. By analyzing circuits, the engineer looks to determine the various...

## Have some knowledge to share

If you have some expert knowledge or experience, why not consider sharing this with our community.

By writing an electrical note, you will be educating our users and at the same time promoting your expertise within the engineering community.

To get started and understand our policy, you can read our How to Write an Electrical Note