# How to refer fault levels across a transformer

By on

Over the past year or so I have been involved in on going discussions related to referring fault levels from the secondary of a transformer to the primary side. While this is easy for some people to grasp, for others it's not so straight forward. Here is a brief explanation of how to do this.

The image shows a simple electrical system around a transformer (primary voltage VP, secondary VS).  A fault, IFS (shown on the secondary), will also been seen on the primary side of the transformer IFP.  Because, the voltage level on the primary of the transformer is different than the secondary, the two values of current will be different.

The value of the primary side fault current is determined by the ratio of the transformer voltages:

That really all there is to it.  If you wanted to refer from the primary to the secondary, just reverse the ratio of the voltages.

## Proof of correctness

To verify that the above is true, consider the power (S) transfer from the primary to the secondary of the transformer; shown by the green line.  The power is the flow of energy into the fault and the 'law of conservation of energy' states that the energy entering the system must be the same as that exiting the system.

Ignoring losses (which are small compared to the fault), the power (energy) into the fault must be supplied by via the primary of the transformer and is the same on both sides of the transformer.

In a single phase system, the electrical power is given by:

applying to both the primary and secondary circuits:

which can be rearranged to give:

For a three phase system (with a symmetrical three phase fault), we have the same result.  The power would be three times that of a single phase system, with voltages as line to neutral.  The three on both sides of the equation cancel, leaving the same answer.

For three phase systems, unbalanced or earth faults are more problematic.  In these instance it is better to use techniques such as symmetrical components to calculate what is happening.

If you need a little more information on working three phase power from single phase power, you can see:

More interesting Notes:

Steven has over twenty five years experience working on some of the largest construction projects. He has a deep technical understanding of electrical engineering and is keen to share this knowledge. About the author

myElectrical Engineering

#### View 3 Comments (old system)

1. Ella says:
3/6/2013 1:35 PM

If I have a Ynd1 transformer and a phase to phase fault exists on the secondary side am I correct to assume that the fault current at the primary side can be represented as a 3 phase fault with a ratio of Vs/2Vp ?

• Steven says:
3/10/2013 9:50 AM

The above applies to balanced faults. With an unbalanced fault such as yours, the primary currents will also be unbalanced.

2. Ella says:
3/11/2013 12:20 PM

Thanks for the feedback. Regarding primary currents in unbalanced situations I am trying to understand distribution of fault currents through transformers. If I have a wye grounded - delta transformer with a phase to earth fault on the secondary side, am I correct to assume that the primary fault currents on the wye side will be 0 through each of the lines?

Furthermore, if the delta side (of the wye groudned delta transformer) is grounded through a zig-zag transformer will the primary currents still be 0?

Thanks
Ella

Comments are closed for this post:
• have a question or need help, please use our Questions Section
• spotted an error or have additional info that you think should be in this post, feel free to Contact Us

Difference Between Live and Dead Tank Circuit Breakers

A quick post in connection with an email question: Live Tank - the circuit breaker the switching unit is located in an insulator bushing which is live...

Network Theory – Introduction and Review

In electrical engineering, Network Theory is the study of how to solve circuit problems. By analyzing circuits, the engineer looks to determine the various...

How to Size Power Cable Duct

Some colleagues had an issue earlier in the week on sizing conduits to be cast in concrete for some power cables . It became clear that none of us had...

How a Digital Substation Works

Traditionally substations have used circuit breakers, current transformers (CT), voltage transformers (VT) and protection relays all wired together using...

Post Editing Tips

If you at all familiar with programs like office and outlook, then adding and editing posts is pretty straightforward and intuitive.  However, there are...

Lightning Risk Assessment (IEC 62305)

IEC 62305 'Protection against lightning' requires a risk assessment be carried out to determine the characteristics of any lightning protection system...

Railway Electrification Voltages

This post is quick introduction and overview to different railway electrification voltages used in answer to a question sent in via email. While there...

UPS Sizing - Rules of Thumb

It wasn't so long ago I was telling someone that I don't use rules of thumb as most things are easily calculated anyhow.   As it turns out I last week...

Electrical Engineering

Electrical engineering is a field that covers a wide variety of sub-fields, including electricity and electronics. It is a field that goes back to the...

Medium Voltage Switchgear Room Design Guide

Many medium voltage (MV) indoor switchgear rooms  exist worldwide. The complexity of these rooms varies considerably depending on location, function and...

## Have some knowledge to share

If you have some expert knowledge or experience, why not consider sharing this with our community.

By writing an electrical note, you will be educating our users and at the same time promoting your expertise within the engineering community.

To get started and understand our policy, you can read our How to Write an Electrical Note