# How to refer fault levels across a transformer

By on

Over the past year or so I have been involved in on going discussions related to referring fault levels from the secondary of a transformer to the primary side. While this is easy for some people to grasp, for others it's not so straight forward. Here is a brief explanation of how to do this.

The image shows a simple electrical system around a transformer (primary voltage VP, secondary VS).  A fault, IFS (shown on the secondary), will also been seen on the primary side of the transformer IFP.  Because, the voltage level on the primary of the transformer is different than the secondary, the two values of current will be different.

The value of the primary side fault current is determined by the ratio of the transformer voltages:

That really all there is to it.  If you wanted to refer from the primary to the secondary, just reverse the ratio of the voltages.

## Proof of correctness

To verify that the above is true, consider the power (S) transfer from the primary to the secondary of the transformer; shown by the green line.  The power is the flow of energy into the fault and the 'law of conservation of energy' states that the energy entering the system must be the same as that exiting the system.

Ignoring losses (which are small compared to the fault), the power (energy) into the fault must be supplied by via the primary of the transformer and is the same on both sides of the transformer.

In a single phase system, the electrical power is given by:

applying to both the primary and secondary circuits:

which can be rearranged to give:

For a three phase system (with a symmetrical three phase fault), we have the same result.  The power would be three times that of a single phase system, with voltages as line to neutral.  The three on both sides of the equation cancel, leaving the same answer.

For three phase systems, unbalanced or earth faults are more problematic.  In these instance it is better to use techniques such as symmetrical components to calculate what is happening.

If you need a little more information on working three phase power from single phase power, you can see:

More interesting Notes:

Steven has over twenty five years experience working on some of the largest construction projects. He has a deep technical understanding of electrical engineering and is keen to share this knowledge. About the author

myElectrical Engineering

#### View 3 Comments (old system)

1. Ella says:
3/6/2013 1:35 PM

If I have a Ynd1 transformer and a phase to phase fault exists on the secondary side am I correct to assume that the fault current at the primary side can be represented as a 3 phase fault with a ratio of Vs/2Vp ?

• Steven says:
3/10/2013 9:50 AM

The above applies to balanced faults. With an unbalanced fault such as yours, the primary currents will also be unbalanced.

2. Ella says:
3/11/2013 12:20 PM

Thanks for the feedback. Regarding primary currents in unbalanced situations I am trying to understand distribution of fault currents through transformers. If I have a wye grounded - delta transformer with a phase to earth fault on the secondary side, am I correct to assume that the primary fault currents on the wye side will be 0 through each of the lines?

Furthermore, if the delta side (of the wye groudned delta transformer) is grounded through a zig-zag transformer will the primary currents still be 0?

Thanks
Ella

Comments are closed for this post:
• have a question or need help, please use our Questions Section
• spotted an error or have additional info that you think should be in this post, feel free to Contact Us

Photovoltaic (PV) Panel - Performance Modelling

In an earlier note on the site [Photovoltaic (PV) - Electrical Calculations], the theory of solar (PV) cell calculations was introduced.  In particular...

Fault Calculation - Symmetrical Components

For unbalance conditions the calculation of fault currents is more complex. One method of dealing with this is symmetrical components. Using symmetrical...

Operational Amplifier

The fundamental component of any analogue computer is the operational amplifier, or op amp. An operational amplifier (often called an op-amp,) is a high...

Cable Insulation Properties

Cable insulation is used to provide electrical separation between conductors of  a cable.  During the historical development of cables, numerous types...

DC Component of Asymmetrical Faults

The image (reproduced from IEC 60909) shows a typical fault in an ac system.  From the illustration it can seen that there is an initial dc component ...

New Mail Chimp

We've been sending out Newsletters on a regular basis for a few weeks now. To do this we have been using Google's Feedburner service. While Feedburner...

Arc Flash Calculations

Working in the vicinity of electrical equipment poses an hazard. In addition to electric shock hazard, fault currents passing through air causes Arc Flash...

Electric Motors

Collection of links to various places with useful motor information. I’ll try and return to the page every now and again to update it with any motor notes...

Cable Sizing Tool

Our cable sizing tool is one of the more popular tools on the site.  The tool enables cables to be sized in compliance with BS 7671 (the IEE Wiring Regulations...

Laplace Transform

Laplace transforms and their inverse are a mathematical technique which allows us to solve differential equations, by primarily using algebraic methods...

## Have some knowledge to share

If you have some expert knowledge or experience, why not consider sharing this with our community.

By writing an electrical note, you will be educating our users and at the same time promoting your expertise within the engineering community.

To get started and understand our policy, you can read our How to Write an Electrical Note