# Fault Calculation - Symmetrical Components

By on

Symbol - Definition
- system voltage

, , - unbalanced voltages
, , - symmetrical voltages
- circuit impedance

- earth fault impedance

- positive sequence impedance
- negative sequence impedance
- zero sequence impedance

For unbalanced conditions, the calculation of fault currents is more complex. One method of dealing with this is symmetrical components. Using symmetrical components, the unbalanced system is broken down into three separate symmetrical systems:

• Positive sequence – where the three fields rotate clockwise
• Negative sequence – where the three fields rotate anti-clockwise
• Zero sequence – a single field which does not rotate

The positive sequence network rotates clockwise, with a phase of 120° between phases as per any standard a.c. system.

The negative sequence network rotates anti-clockwise, and the zero sequence network with each phase together (0° apart).

### Basic Symmetrical Component Theory

Mathematically, the relationship between the symmetrical networks and the actual electrical systems, make use of a rotational operator, denoted by a and given formally by:

Perhaps more simply, the a operator can be looked at as a 120° shift operator. It can also be shown that the following conditions hold true:

By using the a operator, any unbalanced any unbalance three-phase system Va, Vb, Vc can be broken down into three balanced (positive, negative and zero sequence) networks V1, V2, V0.

Unbalanced Network Symmetrical Network

The operator a, is the unit 120° vector: a = 1|120°. Note: a3=1 and a-1 = a2

### Fault Solutions

Once the sequence networks are known, the determination of the magnitude of the fault is relatively straightforward.

The a.c. system is broken down into it's symmetrical components as shown above.  Each symmetrical system is then individually solved and the final solution obtained by superposition of these (as shown above).

For the more common fault conditions,  once the sequence networks are known, we can jump directly to the fault current.  During a fault and letting Un, be the nominal voltage across the branch, the use of symmetrical components gives the following solutions (excluding fault impedance):

Type of Fault Initial Fault Current Comments
three phase
phase to phase
phase to phase
phase to phase to earth

Note: the example given assumes a phase to phase fault between L2 and L3 (then shorted to earth)

### Sequence Impedance Data

Positive, negative and zero sequence impedance data is often available from manufacturers.

A common assumption is that for non-rotating equipment the negative sequence values are taken to be the same as the positive.

Zero sequence impedance values are closely tied to the type of earthing arrangements and do vary with equipment type.  While it is always better to use actual data, if it is not available (or at preliminary stages), the following approximations can be used:

Element Z(0)
Transformer
No neutral connection ∞ (infinity)
Yyn or Zyn 10 to 15 x X(1)
Dyn or YNyn X(1)
Dzn or Yzn 0.1 to 0.2 x X(1)
Rotating Machine
Synchronous 0.5 x Z(1)
Asynchronous zero
Transmission Line 3 x Z(1)

Approximate Zero Sequence Data (source: Schneider)

## Related Notes

More interesting Notes:

Steven has over twenty five years experience working on some of the largest construction projects. He has a deep technical understanding of electrical engineering and is keen to share this knowledge. About the author

myElectrical Engineering

New Mail Chimp

We've been sending out Newsletters on a regular basis for a few weeks now. To do this we have been using Google's Feedburner service. While Feedburner...

Electromagnetic Compatibility (EMC)

Electromagnetic compatibility (EMC) is the study of coordinating electromagnetic fields give off equipment, with the withstand (compatibility) of other...

GE's Shingijutsu Factory

GE's latest thinking on product manufacturing is he Shingijutsu philosophy or Lean production system. They have started applying this at the Louisville...

EU Code of Conduct on Data Centres - Best Practices

The European Union is implementing a voluntary code of practice for participants with the aim of improving the overall efficiency of data centres. As part...

Three Phase Power Simplified

A single phase system is perhaps the most common type of system most people are familiar with. This is what people have in their homes and what appliances...

Periodic Electrical Installation Inspection – What to Inspect?

This is the second post in a series of two on periodic electrical inspections. In the first post, I discussed how often inspections should be carried out...

IEC Reference Designations

The IEC publishes a series of documents and rules governing the preparation of documents, drawings and the referencing of equipment.   Depending on country...

International System of Units (SI System)

The International System of Units (abbreviated SI) is the world's most widely used system of units.  The system consists of a set of units and prefixes...

How to measure power supply quality

If your are ever called out to troubleshoot something on your electrical system, one of the first things consider is the supply voltage. You want to ensure...

Fault Calculations - Typical Equipment Parameters

A frequent problem in fault calculations is the obtaining of equipment parameters.  While it is always preferable to use the actual parameters of the equipment...

## Have some knowledge to share

If you have some expert knowledge or experience, why not consider sharing this with our community.

By writing an electrical note, you will be educating our users and at the same time promoting your expertise within the engineering community.

To get started and understand our policy, you can read our How to Write an Electrical Note