# How to Calculate Motor Starting Time

By on

Requests to look at induction motor starting time have come up a few times on the site.  Hopefully in this post, I give you guys some idea on how to calculate this.  Failing that, hopefully at least some understanding that it is feasible.

## Starting Time - it's a little complicated

Later in the article I'll give a formula which you can apply to get an approximate starting time.  Prior to that it is worthwhile looking at a few of the influences which make accurate calculation more difficult.

Motor Torque Speed Curve

The first thing to look at is the motor characteristic.  The image shows a typical motor torque curve and a hypothetical load torque curve superimposed .  The torque available to accelerate the motor up to speed is given by the difference between motor torque and load torque:

Where

Ca -  torque to accelerate the motor, N.m

CM – motor torque, N.m

As can be seen, as the speed increases both the motor and load torque vary.   The motor torque characteristic is also a function of the design and construction of the motor and can vary significantly for motors of the same rating.  Starting methods (see Motor Starting - Introduction) also affect the available motor torque and can even affect the shape of the curve.

Any torque used for acceleration, needs to overcome both the inertia of the motor and the load.   By using this and knowing and a bit of mechanical engineering (see the reference below), it is possible to derive an equation for the time to accelerate  from zero to the running speed:

Where:
ta – time to accelerate to running speed, s

nr – motor running speed, rpm
CM – motor torque, N.m
JM – inertia of the motor, kg.m2
JL – inertia of the load, kg.m2

From the above, if you know the motor and load inertias and both the motor and load torque as a function of speed (CM(n), CL(n)) you can calculate the starting time.  While it is possible you could do this by solving the equation for an exact solution, in practice you would generally use some numerical solution or piecewise approximation.

With any complexity on the torque curves or starting arrangement, it is obvious that it is not a trivial matter to calculated the time.  For larger or particularly important motors, the effort of dealing with this complexity would be justifiable.  If required, there are software tools available to assist in the calculation.

## Starting Time - an easier [rough] approximation

By introducing some simplifications, it is possible to have an easier to use formulae to give an approximation for the starting time.

The first simplification is to use an average value of motor torque,

Where
CS - the inrush torque, N.m
Cmax - the maximum torque, N.m

Both these figures are available from the manufacturer.

For reduced voltages, torque is reduced by the square of the reduction, so It should be possible to adjust the average torque for reduced voltage starting (i.e. star-delta).

The second simplification is to use an adjustment factor KL  to take care of varying load torque CL due to speed changes:

Lift

Fans

Piston
Pumps

Flywheel

1

0.33

0.5

0

Using the simplifications, the approximate starting time is given by:

Where Cacc is the effective acceleration torque and is given by:

An example will show how this works:

A 90 kW motor is used to drive a fan.  From the motor manufacturer and mechanical engineer we have:

• Motor Rated Speed (nr) - 1500 rpm
• Motor Full Load Speed - 1486 rpm
• Motor Inertial (JM) - 1.4 kg.m2
• Motor Rated Torque - 549 Nm
• Motor Inrush Torque (CS) - 1563 Nm
• Motor Maximum Torque (Cmax) - 1679 Nm
• Load Inertia (JL) - 30 kg.m2
• Load Torque (CL) - 620 Nm
• Load Factor (KL) - 0.33

In summary, while the calculation of motor starting time accurately is not trivial, it is possible make realistic estimates for the most common starting scenarios by using a few simplifications.  I have also developed a Motor Starting Time Calculator, which you can find under 'Tool's on the menu or use the link here.

If anyone has anything to add, please do so below. It would be particularly interesting if anyone has measured starting times and is able to compare them to those calculated by the above.

## References

• Three-phase asynchronous motors
Bibliography: Three-phase asynchronous motors. Generalities and ABB proposals for the coordination of protective devices. ABB, 2008.

More interesting Notes:

Steven has over twenty five years experience working on some of the largest construction projects. He has a deep technical understanding of electrical engineering and is keen to share this knowledge. About the author

myElectrical Engineering

#### View 4 Comments (old system)

1. Joe Pescatore says:
6/20/2012 4:55 PM

This is a very good example for a common question asked. I was wondering, what load factor should be used for a centrifugal and positive displacemnet pump? Would you use the fan value for a centrifugal and piston for positive displacement?

• Steven says:
6/21/2012 11:00 AM

Joe, thanks for the comment.

I think your assumption of using fan and piston are correct (at least that is what I would do). Need to bear in mind, you will only get an approximate time anyhow - which is good enough for a lot of applications. If you motor is a particularly large, it may be worth doing a more rigorous calculation.

2. Joe says:
7/11/2012 5:50 PM

Does anyone have any good articles that explain how one should size a motor based off a pump curve? I have read in one article to size the motor based on the far runout on the pump curve (max flow with lower head) for centrifugal pumps, is that correct? I was hoping for some good facts to make correct decision for sizing motors?

Comments are closed for this post:
• have a question or need help, please use our Questions Section
• spotted an error or have additional info that you think should be in this post, feel free to Contact Us

Equipment Verification (to IEC Standards)

One of the requirements to ensuring that everything works is to have equipment selected, manufactured and verified [tested] to IEC standards. Not all equipment...

Restricted Earth Fault Protection

The windings of many medium and small sized transformers are protected by restricted earth fault (REF) systems. The illustration shows the principal of...

Electric Motors

Collection of links to various places with useful motor information. I’ll try and return to the page every now and again to update it with any motor notes...

Fault Calculation - Symmetrical Components

For unbalance conditions the calculation of fault currents is more complex. One method of dealing with this is symmetrical components. Using symmetrical...

Periodic Electrical Installation Inspection – How Often?

How often installations are inspected is up to the owner of the installation, provided such durations do not exceed any regulatory maximums in force. ...

Getting Started with Patents

If you have a great idea or invent something the last thing you want is someone to steal the idea. One of the things you can do is protect the intellectual...

How to measure power supply quality

If your are ever called out to troubleshoot something on your electrical system, one of the first things consider is the supply voltage. You want to ensure...

EU Code of Conduct on Data Centres - Best Practices

The European Union is implementing a voluntary code of practice for participants with the aim of improving the overall efficiency of data centres. As part...

ANSI (IEEE) Protective Device Numbering

The widely used United Sates standard ANSI/IEEE C37.2 'Electrical Power System Device Function Numbers, Acronyms, and Contact Designations' deals with...

Michael Faraday (the father of electrical engineering)

Famed English chemist and physicist Michael Faraday was born on September 22, 1791, in Newington Butts, a suburb of Surrey just south of the London Bridge...

## Have some knowledge to share

If you have some expert knowledge or experience, why not consider sharing this with our community.

By writing an electrical note, you will be educating our users and at the same time promoting your expertise within the engineering community.

To get started and understand our policy, you can read our How to Write an Electrical Note