# What is an Open Delta Transformer

By on

In three phase systems, the use of transformers with three windings (or legs) per side is common.  These three windings are often connected in delta or star, resulting in common transformer configurations such as delta-delta or delta-star.  An open delta transformer is a special arrangement which uses only two windings.

If your new to transformers, have a look at the Power Transformers - An Introduction note.

## Transformer Configuration

The illustration shows how an open delta transformer is connected.  On both the primary and secondary there are only two windings.  Even in this configuration, it is still possible to transform a three phase voltage.

Open Delta Transformer

Open delta transforms are not the commonly used.  Typically they would be used for small loads where cost is important.  Alternatively, they could be used as an emergency measure, should one winding only of a transformer fail.

Sometimes you may hear an open delta transformer referred to as a V-connection transformer.

## Power Delivered

Sometimes the power delivered by an open delta transformer is compared to that of an equivalent three winding transformer.  Typically figures like having 57.7% of the capacity of an equivalent three winding transformer or 87% of two transformers (same winding size) are quoted. While you can think of the transformer in this manner, it is more fruitful not to consider comparisons but to the necessary calculations on the open delta transformer.

Consider the illustration, showing the output from both a close delta and open delta transformer.  Note, that in the delta connection to line current is √3 times the phase current, whereas in the open delta, they are the same.

The transformer output power (in VA) is for a balanced transformer system for the closed delta connection (using phase current), this give:

$VA=3 V L I ph$

And for the open delta connection:

$VA= 3 V L I ph$

Taking the ratio of open delta to closed delta power, gives:

$3 V L I ph 3 V L I ph =0.577 (or 57.7%)$

## Summary

Open delta transformers are three phase devices, with only two windings on each of the primary and secondary sides.  While cheaper than a conventional three winding transformer, the open delta will only deliver 57.7%  of the power of a conventional transformer (not two thirds, 66.7% as may be expected).  There is limited adoption of open delta transformers, although they can be useful in certain situations.

More interesting Notes:

Steven has over twenty five years experience working on some of the largest construction projects. He has a deep technical understanding of electrical engineering and is keen to share this knowledge. About the author

myElectrical Engineering

Photovoltaic (PV) Panel - Performance Modelling

In an earlier note on the site [Photovoltaic (PV) - Electrical Calculations], the theory of solar (PV) cell calculations was introduced.  In particular...

Cables for MV Power Distribution - Earthed versus Unearthed Systems

Power cables can basically be classified into earthed and unearthed cables, where earthed and unearthed refer to the application for which the cable is...

Introduction to Current Transformers

Current transformers (CTs) are used to convert high level currents to a smaller more reasonable level for use as inputs to protection relays and metering...

LED Replacement Light Bulb

The inventor of the first visible light-emitting diode makes history again this year as it begins to show customers a 40-watt replacement GE Energy Smart...

Fault Calculations - Typical Equipment Parameters

A frequent problem in fault calculations is the obtaining of equipment parameters.  While it is always preferable to use the actual parameters of the equipment...

Cable Insulation Properties

Cable insulation is used to provide electrical separation between conductors of  a cable.  During the historical development of cables, numerous types...

Calculating Cable Fault Ratings

When selecting a cable, the performance of the cable under fault conditions is an important consideration. It is important that calculations be carried...

What is LED?

Light Emitting Diodes (LED ) are increasing gaining favour in both the domestic and commercial sectors; due to their efficiency, sustainability and durability...

Why is electricity so hard to understand?

It's been a busy few months on different projects or busy couple of decades depending on how I look at it. I can say that on the odd (frequent) occasion...

Fault Calculations - Introduction

Fault calculations are one of the most common types of calculation carried out during the design and analysis of electrical systems. These calculations...

## Have some knowledge to share

If you have some expert knowledge or experience, why not consider sharing this with our community.

By writing an electrical note, you will be educating our users and at the same time promoting your expertise within the engineering community.

To get started and understand our policy, you can read our How to Write an Electrical Note