# What is an Open Delta Transformer

By on

In three phase systems, the use of transformers with three windings (or legs) per side is common.  These three windings are often connected in delta or star, resulting in common transformer configurations such as delta-delta or delta-star.  An open delta transformer is a special arrangement which uses only two windings.

If your new to transformers, have a look at the Power Transformers - An Introduction note.

## Transformer Configuration

The illustration shows how an open delta transformer is connected.  On both the primary and secondary there are only two windings.  Even in this configuration, it is still possible to transform a three phase voltage.

Open Delta Transformer

Open delta transforms are not the commonly used.  Typically they would be used for small loads where cost is important.  Alternatively, they could be used as an emergency measure, should one winding only of a transformer fail.

Sometimes you may hear an open delta transformer referred to as a V-connection transformer.

## Power Delivered

Sometimes the power delivered by an open delta transformer is compared to that of an equivalent three winding transformer.  Typically figures like having 57.7% of the capacity of an equivalent three winding transformer or 87% of two transformers (same winding size) are quoted. While you can think of the transformer in this manner, it is more fruitful not to consider comparisons but to the necessary calculations on the open delta transformer.

Consider the illustration, showing the output from both a close delta and open delta transformer.  Note, that in the delta connection to line current is √3 times the phase current, whereas in the open delta, they are the same.

The transformer output power (in VA) is for a balanced transformer system for the closed delta connection (using phase current), this give:

$VA=3 V L I ph$

And for the open delta connection:

$VA= 3 V L I ph$

Taking the ratio of open delta to closed delta power, gives:

$3 V L I ph 3 V L I ph =0.577 (or 57.7%)$

## Summary

Open delta transformers are three phase devices, with only two windings on each of the primary and secondary sides.  While cheaper than a conventional three winding transformer, the open delta will only deliver 57.7%  of the power of a conventional transformer (not two thirds, 66.7% as may be expected).  There is limited adoption of open delta transformers, although they can be useful in certain situations.

More interesting Notes:

Steven has over twenty five years experience working on some of the largest construction projects. He has a deep technical understanding of electrical engineering and is keen to share this knowledge. About the author

myElectrical Engineering

Cable Sheath and Armour Loss

When sizing cables, the heat generated  by losses within any sheath or armour need to be evaluated. When significant, it becomes a factor to be considered...

Microsoft OneNote

A couple of months ago I came Microsoft's OneNote and downloaded the 60 day free trail. Since then I have been using it regularly and now have a full license...

Load Flow Study – how they work

A load flow study is the analysis of an electrical network carried out by an electrical engineer. The purpose is to understand how power flows around...

What is Aircraft Ground Power

Ever wondered what kind of power an aircraft uses when parked at the airport stand. Normally the aircraft generates it own power, but when parked with...

Random Numbers

Using laser optical pulses the random number generator utilizes the time between arrival of random photos to generate the numbers, ensuring true accuracy...

International System of Units (SI System)

The International System of Units (abbreviated SI) is the world's most widely used system of units.  The system consists of a set of units and prefixes...

8 Steps to Low Voltage Power Cable Selection and Sizing

A recurring theme on our forums is cable sizing. Now many installations are unique and require special consideration. However, a lot of the time things...

Periodic Electrical Installation Inspection – How Often?

How often installations are inspected is up to the owner of the installation, provided such durations do not exceed any regulatory maximums in force. ...

Power Transformers - An Introduction

One of the fundamental requirements of an alternating current distribution systems it to have the ability to change the magnitude of voltages.  It is more...

Paternoster Lifts

These lifts were first built in 1884 by J. E. Hall and called a paternoster ("Our Father", the first two words of the Lord's Prayer in Latin) due to its...

## Have some knowledge to share

If you have some expert knowledge or experience, why not consider sharing this with our community.

By writing an electrical note, you will be educating our users and at the same time promoting your expertise within the engineering community.

To get started and understand our policy, you can read our How to Write an Electrical Note