What is an Open Delta Transformer

By on

In three phase systems, the use of transformers with three windings (or legs) per side is common.  These three windings are often connected in delta or star, resulting in common transformer configurations such as delta-delta or delta-star.  An open delta transformer is a special arrangement which uses only two windings.

If your new to transformers, have a look at the Power Transformers - An Introduction note.

Transformer Configuration

The illustration shows how an open delta transformer is connected.  On both the primary and secondary there are only two windings.  Even in this configuration, it is still possible to transform a three phase voltage.

Open Delta Transformer

Open delta transforms are not the commonly used.  Typically they would be used for small loads where cost is important.  Alternatively, they could be used as an emergency measure, should one winding only of a transformer fail.

Sometimes you may hear an open delta transformer referred to as a V-connection transformer.

Power Delivered

Sometimes the power delivered by an open delta transformer is compared to that of an equivalent three winding transformer.  Typically figures like having 57.7% of the capacity of an equivalent three winding transformer or 87% of two transformers (same winding size) are quoted. While you can think of the transformer in this manner, it is more fruitful not to consider comparisons but to the necessary calculations on the open delta transformer.

Consider the illustration, showing the output from both a close delta and open delta transformer.  Note, that in the delta connection to line current is √3 times the phase current, whereas in the open delta, they are the same.

The transformer output power (in VA) is for a balanced transformer system for the closed delta connection (using phase current), this give:

$VA=3 V L I ph$

And for the open delta connection:

$VA= 3 V L I ph$

Taking the ratio of open delta to closed delta power, gives:

$3 V L I ph 3 V L I ph =0.577 (or 57.7%)$

Summary

Open delta transformers are three phase devices, with only two windings on each of the primary and secondary sides.  While cheaper than a conventional three winding transformer, the open delta will only deliver 57.7%  of the power of a conventional transformer (not two thirds, 66.7% as may be expected).  There is limited adoption of open delta transformers, although they can be useful in certain situations.

More interesting Notes:

Steven has over twenty five years experience working on some of the largest construction projects. He has a deep technical understanding of electrical engineering and is keen to share this knowledge. About the author

myElectrical Engineering

Introduction to Traction Substations

Following on from my post on railway electrification voltages, I thought an introduction to traction substations would be a good idea. Traction substations...

Restricted Earth Fault Protection

The windings of many medium and small sized transformers are protected by restricted earth fault (REF) systems. The illustration shows the principal of...

DC Motor Operation

Coils of wire on the rotor carry a d.c. current which generates a magnetic field. A stator magnetic field is created using either permanent magnets or...

For the past few years I have reading eBooks on my HTC touch phone. On and off I have debated buying an eReader and recently purchased a Sony PRS-300 ...

myElectrical - Cable Sizing Tool Upgrade

Our IEE cable sizing was wrote a few years ago and had become rough around the edges. I thought it was time to give the tool a service. Unfortunately when...

Fault Calculation - Symmetrical Components

For unbalance conditions the calculation of fault currents is more complex. One method of dealing with this is symmetrical components. Using symmetrical...

Motor Efficiency Classification

Electric motors are one of the most widely used items of electrical equipment. Improving motor efficiency benefits include, reduced power demand, lower...

Lead acid batteries are cost effect and reliable, making them suitable for many applications.This note examines topics of interest associated with the...

Star-Delta Motor Starting - Performance

Many questions sent in to the site are in connection with motor starting and in particular star-delta.  For all but the simplest application, there is...

Aluminium Windings - Dry Type Transformers

The other day I was talking to a colleague who is a building services consultant.  Despite regularly specifying dry-type/cast resin transformers he was...

Have some knowledge to share

If you have some expert knowledge or experience, why not consider sharing this with our community.

By writing an electrical note, you will be educating our users and at the same time promoting your expertise within the engineering community.

To get started and understand our policy, you can read our How to Write an Electrical Note