# UPS Battery Sizing

By on

Various techniques exist to enable the correct selection of batteries for UPS applications. The procedure described below is one of the more common.  It is also possible to use the IEEE 485 method (see link at the bottom of the page).

## Battery Types

Typically the following battery types are used in UPS systems:

• Lead Acid/Calcium, Maintenance-free Liquid Electrolyte Battery
• Lead Acid/Calcium, Maintenance-free Gelled Electrolyte, Sealed Battery
• Lead Acid (Special Alloy), Suspended Electrolyte, Maintenance-free, Sealed Battery
• Nickel Cadmium, Pocket Plate Liquid Electrolyte Battery

## Battery Sizing

Example of UPS battery sizing

Select the battery model number and quantity (using the typical watts per cell table) for a 300 kVA UPS, 94% efficiency, power factor of 0.8, for a backup time of 15 minutes.

The UPS battery bus voltage is 480 V. The typical table is for 12 V batteries (six cells of 2 V each).

Quantity of batteries per bank = 480/12 = 40 batteries

Number of cells per bank = 40 x 6 = 240 cells

Looking at the capacity, we see that the required watt/cell is too much for one bank. However, various options are available, for example if we decided to use three banks in parallel:

watt/cell (three banks in parallel) = 1063/3 = 354
- select a S12V370(F) battery

Total number of batteries required
= 40 (per bank) x 3 (banks) = 120

Manufacturers provide sizing information for their batteries. Generally this information assumes a room temperature of 25oC. Batteries which will be operated at different temperatures continuously should be calculated specifically for that temperature.

Batteries are generally sized using [Watts] per cell or on [Ampere] per cell.

### Watts per cell method

Normally information supplied for lead acid batteries designed for short discharge times (5-120 minutes) is in the form of kilowatts per cell tabulated for various back-up times. The required [Watts] per cell are given by:

Where:
VA    = VA of the load
pf     = power factor
η      = efficiency of the UPS
N     = Number of cells

Typical Performance Specification (Amperes per Cell @25 °C)

### Amperes per cell

Average Battery Voltage

Battery voltage varies in use - staring high and then decreasing to it's end of discharge voltage.  Taking into account this variation, makes calculation more complicated.

More often, an average voltage value is taken and calculations based on this.

If unsure about what the average value to use, then the end of discharge voltage could be used (as this is on the safe side).

Long term discharge lead acid batteries and most nickel cadmium batteries are sized using charts expressed in available amps for specified periods of time. The required [Amperes] per cell is:

Where:
VA    = VA of the load
pf     = power factor
η      = efficiency of the UPS inverter (dc to ac)
Vdc   = Average Discharge Voltage

Typical Performance Specification (Amperes per Cell @25 °C)

## Battery Charger Sizing

In general, a short term discharge battery can be recharged to 85% capacity in 8-10 times the discharge time. A long term discharge battery can be recharged to 85% capacity in a minimum of 8 hours provided the charger is sized properly.

Assuming the UPS is float charging, the following charging current Ic  is required:

Given:

and

Where:
Ic = Charging current
IB = Battery current required
Td = Battery discharge (run) time
k = Safety factor (typically 1.5)
Tr = Battery recharge time
Ii = Inverter current required

More interesting Notes:

Steven has over twenty five years experience working on some of the largest construction projects. He has a deep technical understanding of electrical engineering and is keen to share this knowledge. About the author

myElectrical Engineering

#### View 6 Comments (old system)

1. vinh says:
3/29/2013 5:50 AM

it is OK in general but is better with examples,
Especially "Vdc = Average Discharge Voltage" . What is average Disc volt?

• Steven says:
3/31/2013 2:46 PM

Thanks for the suggestions. I've added a quick example to the post - hopefully it will help.

2. Vinh says:
4/2/2013 11:22 AM

Steven,
Thanks for the example.
One thing I'm not sure is why real power P (watt), instead of apparent power S (VA), is used to size the batteries.
If P is used then where the Q power (VAR) comes from?
Vinh

• Steven says:
4/4/2013 4:52 AM

In a d.c. system there is no reactive power. As the batteries are d.c. I think it just makes sense to use Watts for the calculation.

Reactive power for the a.c. would have to be generated by the UPS.

3. senthil kumar says:
5/8/2013 1:42 PM

How to do maintenance for battery long life.

4. Notes says:
8/21/2013 3:21 PM

A UPS is an uninterruptible power supply.  It is a device which maintains a continuous supply of electrical power, even in the event of failure of the mains (utility) supply.  A UPS is installed between the mains supply and the equipment to be protected... ...

Comments are closed for this post:
• have a question or need help, please use our Questions Section
• spotted an error or have additional info that you think should be in this post, feel free to Contact Us

Harmonised Cable Codes and Colours

Within Europe the European Committee for Electrotechnical Standardization (CENELEC) has standardised the both the designation and colour of cables.   ...

DC Motor Operation

Coils of wire on the rotor carry a d.c. current which generates a magnetic field. A stator magnetic field is created using either permanent magnets or...

The 27 km, Euro 6 billion  Collider lies on the border between France and Switzerland, took nearly 30 years to complete.  Some of the lofty goals for the...

Photovoltaic (PV) Panel - Performance Modelling

In an earlier note on the site [Photovoltaic (PV) - Electrical Calculations], the theory of solar (PV) cell calculations was introduced.  In particular...

IEC Reference Designations

The IEC publishes a series of documents and rules governing the preparation of documents, drawings and the referencing of equipment.   Depending on country...

Tip – Latitude and Longitude on Large Scale Plans

If you are working on a large plan, get the real coordinates [latitude, longitude] for two or more points and add them to the drawing. That way you can...

Are We Losing Professional Integrity

I have been thinking recently that there appears to be less professional integrity around than when I first started my career in electrical engineering...

Equipment Verification (to IEC Standards)

One of the requirements to ensuring that everything works is to have equipment selected, manufactured and verified [tested] to IEC standards. Not all equipment...

Random Numbers

Using laser optical pulses the random number generator utilizes the time between arrival of random photos to generate the numbers, ensuring true accuracy...

Tech Topics/Application Notes - Siemens

There are a lot of interesting two page type notes on various medium voltage topics – switchgear, circuit breakers, bus systems etc. It is on the Siemens...

## Have some knowledge to share

If you have some expert knowledge or experience, why not consider sharing this with our community.

By writing an electrical note, you will be educating our users and at the same time promoting your expertise within the engineering community.

To get started and understand our policy, you can read our How to Write an Electrical Note